- Ochrona przeciwpożarowa
- Telewizja dozorowa
- Systemy alarmowe
- Kontrola dostępu
The DOP-6001 beam smoke detector is designed for smoke detection at the start of a fire. It is especially suitable for protection of indoor spaces, in which the appearance of smoke is likely during ignition of a fire, and where, due to a large space area, installation of a greater number of point smoke detectors would be necessary.
These detectors can operate exclusively in POLON-ALFA manufactured fire alarm system detection lines: directly in addressable loop-shaped lines of the POLON 4000 system, in the IGNIS 1000/2000 system conventional lines..
Principles of operation
The DOP-6001 detector consists of an infrared (IR) light transmitter and a receiver located in a single housing and an interoperating E39-R8 prism reflector or 4xE39-R8 reflector panel.
Operation of the beam smoke detector is based on an analysis of air optical transparency in the space between the detector and the prism reflector or the prism reflector panel. If certain defined content of aerosol (smoke) is found in the air reducing opti al transparency, then the detector, according to a pre-set sensitivity threshold will evoke an alarm mode. Complete interruption of the radiation beam is signalised as a fault mode because even the largest smoke concentration in the air does not cause complete interruption of the detector optical beam path. If the air is clear, the detector is in a quiescent mode. The DOP-6001 beam smoke detector is equipped with a builtin automatic compensation systems for monitoring of dirt build-up on its optical system and compensation for environ impact conditions ensuring that the detector maintains constant sensitivity and fire detection ability for a long time. At a certain level of dirt build-up, the detector signals a fault mode denoting the necessity to undertake servicing and cleaning works.
Communication between the control panel and the detector is executed using a two-wire addressable detection line. The detector is equipped with an internal short circuit isolator. In order to achieve the detector proper functioning, it is necessary to align its optical path. In the case of an addressable detector it is carried out by initiati on of such a process from the POLON 4000 or POLON 6000 system control panel level, or by pressing the START push button (located on the detector) in case the detector operates in a conventional operation mode.
The DOP-6001 beam smoke detector and the prism reflector or reflector panel are installed on opposite walls of a room. Special adjusting screws are provided at the detector and the reflector panel for precise alignment of the detector and the reflector/s in the optical path. A special laser target viewfinder is actuated at the moment when the optical beam path is aligned. The prism reflector and the reflector panel are not included in the order product package and they should be ordered separately.
addressable, conventional, line
to work in normal conditions
10,5 VDC - 24 VDC
|Quiescent current consumption|
max. detector current consumption from conventional line 2,2 mA or 5 mA
|Current consumption in alarm mode|
|Detected test fires|
TF1 to TF5 and TF8
address coding automatically from control panel
|Operating temperature range|
from -25°C to 55°C
to 95% at 40°C
|Dimensions of detector with base|
84 x 128x 79mm
Working range with reflectors unit 4xE39-R8 - 50 to 100m, Working range with reflector E39-R8 - 5 to 50m, Sensitivity thresholds - 18%, 30%, 54%, Number of detectors on conventional line - 1, Laser pointer supply - 6F22 9V battery